The integral RS 485 Serial Port on The Brain® Digital Recirculating Valve (DRV) can be used to connect the DRV to either BrainScan® or directly to a Building Automation System (BAS) which operates on a Modbus protocol.
BrainScan® is an optionally selected control module from
Armstrong which enables an interface with Building Automation Systems
(BAS) which utilize Modbus, Bacnet™ or LonWorks™ protocols via the use
of specific protocessor cards.
BrainScan® also has an ethernet port and operates as a web server for remote network access.
BrainScan® includes remote hot water supply, cold/
recirculation water supply, blended water outlet temperature outputs and
is supplied with a system graphic, memory card for data storage and web
BrainScan® includes terminals for additional installer
supplied RTD’s, pressure transducers and pulse type flow meters and this
data can be forwarded via the BrainScan® interface.
Modbus – DRV can be configured to communicate directly with BAS which use Modbus protocols.
When configured for Modbus the DRV becomes a Remote Terminal Unit (RTU).
The BAS will need to be using a Modbus RTU format.
When connected directly to a BAS using Modbus, the DRV will be
assigned a unique network address which is programmed via the integral
DB9 external port.
The integral RS485 Serial Port provides an ability to remotely program the DRV and update the firmware via BrainScan or Modbus.
The integral RS485 Serial Port can receive the following outputs from the DRV and communicate them via BrainScan or Modbus.
- Set Point
- Inlet/Outlet Temperature
- Over Temperature Alert
The integral RS284 Serial P0rt can receive the following self
diagnostic error messages from the DRV and communicate them via
BrainScan or Modbus
- Over Temperature Error
- PCB Error
- Thermister Error
- Motor Error/Emergency Mode
- Battery Error